IEC 60099-5 PDF
IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||16 June 2016|
|PDF File Size:||14.71 Mb|
|ePub File Size:||19.62 Mb|
|Price:||Free* [*Free Regsitration Required]|
Typical maximum residual voltages are given in Kec F. It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Sustainable Development Goals and standardisation, how do they connect?
IEC | IEC Webstore
Report error on page. An additional section discusses several special methods that may be used to improve lightning performance. What is a standard? Do you need a multi-user copy?
The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition. Message to your colleague.
BS EN – Surge arresters. Selection and application recommendations
The requirements for human safety are not covered by this standard. 6009-5 note that the selected standard is invalid. Surge arresters – Part 5: When you use our service you can be assured the latest editions and easy access. Subscribe on standards with our subscription service.
BS EN 60099-5:2013
You may find similar items within these 6099-5 by selecting from the choices below:. Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a. Learn more about the cookies we use and how to change your settings. Low-voltage limiters are covered under Clause 7.
Surge arresters and low-voltage limiters for specific use in d. Surge protective components, current at the date of this publication.
Subscribe on standards – Read more. Though it will be many years before the both standards are virtually the same, this is a first step. IEC Surge Arresters: Copyright – ArresterWorks.
Its object is to give information in terms of methods, modeling and examples, allowing for the application of the approaches presented in IECand for the selection of insulation levels of equipment or installations, as defined in IEC Contact us svenska Login. It also gives the lists of the standard withstand voltages from which the rated withstand 60099–5 should be selected. It has been years in the making. Worldwide Standards We can source any standard from anywhere in the world.
Shopping cart Close cart 0, foreach: It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
This new edition covers new mechanical test requirements for polymer and porcelain housed arresters. Computational guide to insulation co-ordination and modeling of electrical networks This technical report gives guidance on conducting insulation co-ordination studies which propose internationally recognized recommendations for the numerical modeling of electrical systems including arresters and for the implementation of deterministic and probabilistic methods adapted to the use of numerical programs.
Please download Chrome or Firefox or view our browser tips.
The way these transmission-line choices will improve or degrade lightning performance is also provided. Surge Arresters and subcommittees 37A: The procedures are based on theoretical studies, test results, and experience.