ALTISTART 46 MANUAL PDF
Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Published (Last):||19 July 2005|
|PDF File Size:||2.81 Mb|
|ePub File Size:||19.12 Mb|
|Price:||Free* [*Free Regsitration Required]|
This briefing has to be transmitted to the customer and to DAS and must contain the following information: For floppy disc 2, follow the instructions that will appear on the PC screen. For units with two transformers only the right-hand transformer viewing the unit from the front is to altustart removed.
DZ4DP 16 2 Black wires marks 16 and Remove the connectors located at the base of the product. Cable too long between motor and starter 1.
SY3CM 14 2 clips: Core housing Material U. It’s a community-based project which helps to repair anything.
SBS – Hands on experience. Over Heat Fault starter thermal protection fault. The position of the blue wires aptistart different on an ATS Care should be taken to ensure that this card is positioned correctly, placing the connectors towards the top of the unit.
Altistart 46 – Documents and Downloads | Schneider Electric
Conversion instructions for size 3 9 – Install the connectors in the locations behind the control module of the Altistart according to the markings. Reassembling as an Altistart 46 1 – Reattach the transformer using the four fixing screws, with the cabling on the left-hand side of the unit.
Transformer complies with U. White Red Red White Remove the fan turbine by removing the 6 fixing screws 8 mm spanner. With software version V1. Outlet order is not important. This conversion can only be performed on products dated later than the following weeks: Fan 2 3 0V 1 8 5W Recommended torque load for screw M4: The pump transformer must be removed. This function is only protecting from short-circuits on motor side. During a start-order on contactor with software version inferior to V1.
If the motor runs on RUN order and stops at the 3 stop configurations, without disable, the repair is over. OLF acknoledgement, followed by a start request are done as following: Assembly size 3 Parts list Interconnection drawing Part 4: Assembly size 5 Parts list Part 6: The product structure is identical to the one of ATS23, that is to say, a control element common to all sizes, and a power element specially designed to each calibre.
The time of delivery of the repaired or new element will be given by the dealer or the agency. FrF Frequency Fault Measurement principle: Starter not alfistart with manjal on L1-L2-L3. Only one thyristor in short-circuit. Fan Screw Transformer Conversion instructions for size 3 Remove the thyristor cables. Assembly size 4 Parts list Interconnection drawing Part 5: Phases off-balance due to insulation defect on IT rate 1.
It is also possible to know the software version with PC software.
It suits the one used for Altivar tests. External fault order Operating state Up to now experience: They are also manufactured and tested at Schneider factory at Pacy Blanchet. The motor does not brake the load correctly The motor does not brake the load correctly cause check remedy High inertia After the brake request, there is current into the motor even in a discontinuous way.
Low torque at start tQ0.
If phase rotation fault is selected, check if the phase rotation of the network voltage is in conformity with the one selected direct, indirect, otherwise, the fault is generated. Use of a self maintained bypass with external thermal protection.
Avoid the current pulse in the engine as well as startup in current control correction of the anomaly concerning a random startup following a series of transient power cutoffs. InF recognition of rating Up to now experience: Insert floppy disc 1 in drive A, 3.
Use the fixing points to run the cables along the insulating dividers and connect up to the clips.
User’s manual ATS46
J7 Connector if pump unit J9 J10 J11 rear view of the control module 5 – Remove the connectors from the vigitherm and the current transformers. J 49 Follow the diagram: If, for practical reasons, you do not want to disconnect the protection and control circuits, top to bottom terminal resistance can be measured.
V Insulation varnish must comply with U. Conversion instructions for size 3 8 – Remove the six screws from the fan mounting plate. Do not soak attach brackets in the indicated areas. PiF Phase inversion Fault Measurement principle: